In combination with the new Sunny Portal powered by ennexOS, the Data Manager M optimizes communication, monitoring and control of PV systems with up to 50 SMA devices. Based on the new IoT platform for energy management, ennexOS from SMA, the Data Manager M not only replaces the SMA Cluster Controller S, but its expandability also means that it is already well-equipped to handle the new business models of the energy market of the future. For example, it is the ideal professional system interface for electric utility companies, direct marketers, service technicians and PV system operators.
Particularly impressive is its innovative and highly efficient user interface, which has been standardized for both Data Manager M and the new Sunny Portal powered by ennexOS. A range of intuitive assistance functions for the Data Manager M, inverters and Sunny Portal powered by ennexOS significantly reduce the amount of time involved in commissioning and parameterization.
The basic scope of functions and interfaces offered by the new Data Manager M is coordinated with the associated functions in Sunny Portal powered by ennexOS and adapts to future requirements step by step. Thanks to its modular design and systematic support of industrial standards such as Modbus/TCP, systems can be expanded to include additional components such as I/O systems or energy meters, from either SMA or other suppliers.
Quick and easy
Reliable and convenient
Future-proof and flexible
The Data Manager M and the new Sunny Portal powered by ennexOS are perfectly coordinated with each other. This not only makes it easier to monitor, analyze, parameterize and manage PV systems, but also helps save time and money.
Whether for an entire portfolio, system groups, systems, PV system sections or individual devices, you will find the relevant information for the various user roles on the dashboards in a clearly structured format—at every level
Standard pages for monitoring, analysis and parameterization allow you to work efficiently and help you save time managing your systems.
The preconfigured MOXA and Wago I/O systems available from SMA are perfectly coordinated with the new IoT energy management platform ennexOS and can be easily integrated into a system. Thanks to its high level of flexibility, the system can meet changing customer requirements at any time, for example, if there are any changes in legal or normative requirements.
SMA Data Manager M + Sunny Portal powered by ennex OS
How you benefit:
Expandable thanks to modular design - additional functions will be available since May 2018
|Number of supported devices||25||50|
|Number of logged data points per subdevice||30||Data points vary depending on the connected device|
|Local admin account and access via Sunny Portal accounts||x|
|RS485||-||x||For meters and sensors|
|Inverter field bus||Fast Ethernet (Speedwire)
|Network (LAN)||Fast Ethernet
|WLAN||-||x||WPA2, peer-2-peer connection for commissioning & service purpose|
|Live data in Sunny Portal powered by ennexOS||-||x|
|SMA Data 2+ - Speedwire||x|
|SMA Data 1 - RS485||x||Support of SMA Data 1 through Data Manager in 2019|
|SMA Energy Meter protocol||x|
|DHCP server for field bus||-||x||Separation of SMA plant network from LAN|
|Modbus server SMA profile support (plant level)||x||Modbus-Profil on Unit ID 1 and 2 compatible with CLCON|
|Modbus server SMA profile support (subdevices)||-||x||Sudevices can be addressed directly (no separated networks)|
|Modbus server Sunspec support||-||x|
|FTP Push client||-||x
(once per day)
(15 min interval)
|XML export identical to CLCON format|
|Modbus/RTU (for sensors and meter via RS485)||-||x|
|Remote device parameterization (all SMA components)||x||Via Sunny Portal powered by ennexOS|
|Assistant for plant wide parameterization & parameter comparison (local & remote)||-||x||Via Data Manager M and Sunny Portal powered by ennexOS|
|Parameterization via Modbus (all SMA components)||-||x|
|Update via update portal & USB (Data Manager M)||x|
|Update update portal & USB (SMA equipment)||-||x||SMA inverters (e.g. CORE1) receive their updates directly from SMA update portal|
|Multible meter support||x|
|Custom Modbus/TCP meter support||-||x||Registration with individual Modbus/TCP register|
|Visualization of systems with batteries||x||x||Aggregated view with august 2018 release|
|Diesel genset visualization||-||x|
|Direct seller Modbus interface||x||mit with external VPN router|
|Integrated direct seller interface (SMA SPOT)||-||x|
|Peak load shaving with STPS60||-||x||In combination with SMA Inverter Manager|
|Simple closed-loop control for increased self-consumption with battery systems (STPS60)||-||x||In combination with SMA Inverter Manager|
|Simple closed-loop time-of-use tariff based battery system optimization (STPS60)||-||x|
|EEBus - HVAC support||-||x|
|EEBus - E-mobility support||-||x|
|Setup assistant for grid management services||x|
|Fast stop via digital signal||x||5 digital inputs integrated in EDMM integriert - one reserved for fast stop|
|Active power targets via digital signal||x||5 digital inputs integrated in EDMM integriert - 4 for active power targets|
|Active/reactive power targets via Modbus||x||Via SMA Modbus profile|
|Measured values via Janitza UMG 604||x|
|Measured values via SMA Energy Meter||x|
|Measured values via Elkor WattsOn Mark II||-||x|
|Active/reactive power targets via IEC 61850||-||x||In Combination with Wago PFC200 (IEC61850<->Modbus)|
|Active/reactive power targets via IEC 60870-5-104||-||x||In Combination with Wago PFC200 (IEC60870<->Modbus)|
|Active/reactive power targets via digital or analog signals (8xDI, 3xDO, 2xAI, 2xAO)||-||x||In Combination with MOXA ioLogik E1242 or WAGO 750|
|Active power closed-loop control (including Zero feed-in)||x||In Combination with SMA Energy Meter or Janitza UMG 604 (from August 2018 with any Modbus/TCP meter)|
|Adjustable fallback behavior for missing setpoints/measured values||x|
|Adjustable active power ramp rate||identical ramps (up & down)||different ramps|
|Adjustable P(V) curve||-||x|
|Adjustable P(f) curve||-||x|
|Constant power factor mode||Configuration for every inverter||Central parametrization with assistant|
|Reactive power control as a function of voltage Q(V)||-||x|
|Reactive power control as a function of active power (Q(P))||-||x|
|Power factor as a function of active power (cosPhi(P))||-||x|
|Reactive power closed loop control||-||x|
|Custom Modbus meter registration with user-defined Modbus/TCP registers||-||x|
Check in the settings of the router whether DHCP is enabled. If DHCP cannot be enabled, a static IP address must be assigned to the Data Manager. To do this, connect the Data Manager to a DHCP-capable router outside the PV system and carry out the commissioning. Assign a correct static IP address to the Data Manager (ask your grid administrator). Then connect the Data Manager to the router in the PV system. Now the Data Manager can be reached via the static IP address. Follow the installation assistant steps and make the settings appropriate for your system.
In order to use the I/O system with the Data Manager, the I/O system with its IP address must be disclosed in the Data Manager. To determine the IP address of the I/O system, proceed as follows:
1. Open the command line interpreter on a suitable end device and enter the command "arp-a".
2. The physical address indicates the associated IP address.
The buffer capacitor of the Data Manager's real-time clock might have discharged due to being without voltage supply for a longer time period. Make sure that the Data Manager has access to a time server on the internet to obtain a current time.
The WAGO-I/O-SYSTEM 750 is suitable for connecting Pt100 temperature sensors with two, three or four wires. SMA recommends connecting Pt100 temperature sensors with two wires since the corresponding bus terminal 750-464 is preset to 2-channel measuring technology.
To be able to use the analog inputs of the ioLogik E1242 with the Data Manager, the analog inputs of the ioLogik E1242 must be set to 4 mA to 20 mA (see manufacturer manual).
The ioLogik E1260 from Moxa is suitable for the connection of Pt100 temperature sensors with two or three wires.
When connecting Pt100 temperature sensors with three wires, the measurements are more accurate, especially for long conductor lengths.
When connecting 2-wire Pt100 temperature sensors, SMA recommends connecting a 3-core shielded cable to the Moxa ioLogik E1260. Lead the third conductor close to the Pt100 temperature sensors and connect it to one of the two Pt100 connectors. Connect the cable shield on one side to the grounding conductor on the Moxa ioLogik E1260. The Moxa ioLogik E1260 itself does not have a connection for a grounding conductor. That is why the grounding conductor of the switch cabinet should be used (there should be a grounding conductor on the DIN rail or the enclosure of the switch cabinet).
In case of inaccurate measured values, the inputs of the ioLogik E1260 from Moxa can be individually calibrated via the user interface (see manufacturer manual).
You can use the power supply unit of the Sunny WebBox, SMA Cluster Controller, SMA Com Gateway or the SMA Inverter Manager. You can also use all power supply units that meet the specifications of the datasheet and the Data Manager manual.
No. To be able to detect new devices, the installation assistant of the Data Manager must be started. Devices with different passwords can also be detected in the installation assistant.
No. Only the master data is currently transmitted. For release 2018, it is also planned to allow for transmission of slave data.
For technical reasons, only in-house certificates will be used. Certificates that could be replaced by an intercepting proxy server cannot be verified. Please contact your network administrator to specify the exceptions for the firewall.
To set up zero export, there must be an appropriate energy meter installed at the grid-connection point. Make the following settings on the user interface of the Data Manager:
1. Select the menu item Grid management service in the menu Configuration.
2. Select Active power.
3. Confirm every step with [Continue]
4. Select the operating mode Closed-loop control.
5. Select the signal source Manual control.
6. Enter the value 0 in the field Active power setpoint
7. Enter the value 1 in the field Time interval.
8. Enter the value 100 in the field Active power gradient.
9. In the field Total system power, enter the desired value.
10. Select [Save].
No further settings are necessary. Now you can find a new widget for active power limitation on the system’s dashboard.
Compact system MOXA E1200 series for price-sensitive applications
Modular WAGO I/O system 750 series for more flexibility
Additional devices and protocols will be integrated on an ongoing basis via Modbus/TCP (e.g., Janitza Power Analyser UMG 604).